Experiment 3: Power Transformer Open and Short Circuit Tests
Objectives
 To conduct standard open and short circuit tests in order to ﬁnd the parameters of the equivalent circuit of a transformer.
 Evaluate the regulation and efficiency of the transformer at a given load.
Equipment
 Fluke meter from the stockroom.
 Two scope leads from the stockroom.
 3phase AC Variac.
 One fourwinding single phase transformer. (Model # T1000)
References
 A. Fitzgerald, C. Kinsley, Jr., S. Umans, Electric Machinery, Ch. 1,
6th Edition, McGrawHill Inc., 2005.
 P.C SEN, Principles of Electric Machines and Power Electronics, 3rd Edition, John Wiley, 2013
Background
A power transformer is usually employed for the purpose of converting power, at a ﬁxed frequency, from one voltage to another. If it is used for converting power from a high voltage to a low voltage, it is called a stepdown transformer. The conversion efficiency of a power transformer is extremely high and almost all of the input power is supplied as output power at the secondary winding.
Consider a magnetic core as shown in ﬁgure 3.1, carrying primary and secondary windings having N_{1 }and N_{2 }turns, respectively. When a sinusoidal voltage is applied to the primary winding, a ﬂux Φ will exist in the core which links both the primary and secondary windings, inducing the RMS voltages
The transformer is said to have a transformation ratio
Equivalent Circuit
The transformer may be represented by the equivalent circuit shown in figure 3.2. The parameters may be referred to either the primary or the secondary side. The series resistances R_{1} and R_{2} represent the copper loss in the resistance of the two windings. The series reactances X_{1} and X_{2} are leakage inductances and account for the fact that some of the flux established by one of the windings does not fully couple the other winding. These reactances would be zero if there were perfect coupling between the two transformer windings.
The shunt resistance R_{p} accounts for the core losses (due to hysteresis and eddy currents) of the transformer. The shunt inductance X_{p} is representative of the inductances of the two windings and would be infinite in an ideal transformer if the number of turns of the two windings were to be infinite.
A knowledge of the equivalent circuit parameters permits the calculation of transformer efficiency and of voltage regulation without the need to conduct actual load tests. But experimental data must first be obtained in order to determine those parameters.
It will be confirmed at the conclusion of the first two parts of this experiment that the impedances of the series branch of the transformer equivalent circuit are substantially smaller than the impedances of the parallel branch. Because of this large discrepancy in the magnitudes of the elements we can redraw the equivalent circuit shown in figure 3.2 into that shown in figure 3.3. The errors introduced into calculations using figure 3.3 in place of figure 3.2 are quite insignificant. Furthermore, the large difference in the magnitudes of the transformer parameters allows for the determination of the elements in the series branch using one set of measurements and the elements in the parallel branch using another set of measurements.
Open Circuit Test
The open circuit test is used to determine the values of the shunt branch of the equivalent circuit R_{p} and X_{p} . We can see from figure 3.3 that with the secondary winding left open, the only part of the equivalent circuit that affects our measurement is the parallel branch. The impedance of the parallel branch is usually very high but appears lower when referred to the low voltage side. This test is therefore performed on the low voltage side of the transformer terminals 1 − 1' in ﬁgure 3.3) to increase the current drawn by the parallel branch to a readily measurable level. Besides, the rated voltage on the low voltage side is lower and therefore more manageable.
T1000 transformer has four windings. Create a 1:2 ratio step up transformer by connecting the two primary windings in series and the two secondary windings in series.
This transformer will also be used in the next part of the experiment, so leave the connections intact when the present part is ﬁnished.
This transformer is rated at 1.0 KVA. The rated current is 1000 VA/240 V = 4.16A on the 240 V side and 1000 VA/120 V = 8.32A on the 120 V side.
Instructions
 Connect the circuit as shown in ﬁgure 3.4. Make sure that the low voltage side of the transformer corresponds to the left side of the connection diagram. A low power factor wattmeter should be used.
 Connect the Power Quality Meter to the left side (primary) of the transformer. If a low Power Factor Wattmeter is used, it should be connected also to primary and DVM’s connected to allow measurement of phase voltage (V_{1}) and primary current (I_{P})
 Connect the power supply from the bench panel to the INPUT of the threephase variac and connect the OUTPUT of the variac to the circuit.
 Vary the input voltage starting at 0 V in 20 V increments to go up to 120 V. At each step change, record I_{p} , W_{0} and V_{1} in table 3.1.
 Turn off the variac.
Report
 Complete table 3.1
 Compute the parameters R_{p} and X_{p} at the rated voltage by using
 Find the value s of R_{p} and X_{p} as referred to the high voltage side.
 Plot the noload current I_{p} , magnetizing current I_{m} , core loss W_{0} and noload power factor cos Φ , against the applied voltage V_{1} on the same graph paper.
Table 3.1: Data for open circuit test.  
V_{1} Volts 
I_{p} Amps 
W_{0} Watts 
I_{c} = W_{0 }/ V_{1} Amps 
Amps 
cosφ = W_{0} / V_{1} I_{p} 
20 40 60 80 100 120 





These parameters are referred to the low voltage side.
Short Circuit Test
The short circuit test is used to determine the values R_{s} and X_{s} of the series branch of the equivalent circuit. These impedances are usually very low, but appear higher in value when referred to the high voltage side. This test is consequently performed on high voltage side of the transformer (terminals 2 − 2ʹ in ﬁgure 3.3) in order to keep the current drawn by these impedances at a manageable level.
Table 3.2: Data for the short circuit test.  
I_{s} Amps 
V_{s} Volts 
W_{s} Watts 
4.0 3.5 3.0 2.5 2.0 1.5 1.0 0.5 


Instructions
 Using the 2:1 ratio transformer of the previous part connect the circuit as shown in figure 3.5. Make sure that the high voltage side of the transformer corresponds to the left side (primary) of the connection diagram. Use the voltage terminals ± and 150 V of the standard AC wattmeter, if used.
 Make sure that the variac is turned all the way down before starting this experiment. Turn on the variac.
 Turn the variac up slowly until the current I_{s} (consult figure 3.5) is at the rated value (about 4 amps). Record I_{s}, V_{s} and W_{s} in table 3.2.
 Repeat the previous step by reducing the current I_{s} in 0.5 A and record all values in table 3.2.
 Turn off the variac.
Report
 Plot the copper losses W_{s} against the current I_{s}.
 Compute the equivalent circuit parameter R_{s} and X_{s} at the rated high voltage winding current by first calculating
 Calculate the values of R_{s} and X_{s} referred to low voltage side.
 Now that we have all the parameters for the transformer equivalent circuit, compute the voltage regulation at the rated power and at a lagging power factor of 0.8.
 Calculate the per unit efficiency at the rated power and at a lagging power factor of 0.8.
 Calculate the value of the maximum efficiency of the Transformer and determine the current at which it occurs.
 Using the laboratory data, determine percent efficiency of the Transformer at half rated power and 0.8 lagging power factor.
The above results can then be used to find
These parameters are referred to the high voltage side.